Station drops are equipped with an in-line shut-off valve, drip leg, ball valve and outlet cap and chain. All drops are labeled for the indicated gas service.
To install the Duratec Composite Piping to the Station Drops, all you need is to thread one of the corresponding Duratec Pipe Adapters above (part numbers MP-MTA3434 or CMP-MTA1212) to the top of the Station Valve were the Ball Valve is located. Then the Composite Piping fits into the pipe end of the Adapter.
WARNING: Products on this website can expose you to chemicals including lead which is known to the state of California to cause cancer, birth defects or reproductive harm. For more information, go to www.P65Warnings.ca.gov.